This manual describes diagnostic capabilities and some troubleshooting information for the RediGate industrial data gateway products, including:
The Elecsys gateway products are multi-function communication interface devices, which can be configured for many different types of applications such as protocol conversion, data concentration, and report-by-exception of data. Diagnostics are available to diagnose communication problems and to verify proper operation of every aspect of the system.
Some features described herein may only be available on more recent software releases of the gateway device. Variations between different product models will be distinguished where needed.
This document refers to the gateway configuration or "ACE configuration," which is created and uploaded to the RediGate using the ACE Configuration Editor. See the article Installing ACE and the http://partner.elecsyscorp.com/manuals page for documentation on using ACE to configure the RediGate.
The RediGate typically uses COM0 for a local serial diagnostics port. When the RediGate is powered on, it sends startup messages to its COM0 port. A terminal program must be set up with communication parameters configured for a baud rate of 115,200, no parity, 8 bits, 1 stop bit.
RediGate 100 series: COM0 is available via the Micro-USB port on the front of the device. See the article Installing USB Driver for installing the required USB serial driver in Windows.
RediGate 400 series: COM0 is a DB-9 RS-232 port. Pinout is: pin 3–TX, pin 2–RX, pin 5–GND (use a null modem serial cable to a configuration computer).
In order to use the serial diagnostics (MMI or Linux console) after startup, the following objects are required in the RediGate configuration:
Diagnostics are available through a network connection via a secure shell (SSH) login, typically using IP port 22.
In order to use network diagnostics, the following things are required in the RediGate configuration:
(NOTE: Some cellular account activations do not allow SSH connections to be made to cellular device. Check with your account provider for information on this.
The RediGate diagnostics menu and console are accessed using a terminal program over serial or SSH. There are several terminal programs you can use.
Tera Term: The ACE Configuration Editor (as of version 3.5) includes a built-in option to "Connect to Device." See this article for details: ACE 'Connect to Device' Menu
PuTTY: See these articles for installing and setting up PuTTY:
Setting Up Putty for USB Connection (for RediGate 100 series)
Setting up PuTTY for Serial Communication (for RediGate 400)
Setting up Putty for Network Communication
ExtraPuTTY: Similar to PuTTY, but with additional options such as serial and network file transfer options. Download ExtraPuTTY from http://www.extraputty.com/download.php